Copper Concentric Cable meets or exceeds the following standard:
ICEA S-94-649: Standard forConcentric Neutral Rated Cables 5 – 46 kV.
AEIC CS8: Specifications for Extruded Dielectric, Shielded Power Cable, Rated 5 – 46 kV.
IEC 60502-2: Cables for rated voltages 6KV(Um=7.2KV) upto 30KV(Um=36KV)
Conductor: Soft annealed uncoated copper Class B compressed or unilay compressed per ASTM B8 or hard drawn aluminum Class B compressed or unilay compressed stranding per ASTM B231.
Conductor Shield: Semi conducting cross-linked polyethylene (XLPE).
Insulation: Thermoset tree-retardant cross-linked polyethylene (TR-XLPE).
Insulation Shield: Semi conducting cross-linked polyethylene (XLPE).
Concentric Neutral: Soft annealed solid copper wires per ASTM B3, helically applied and uniformly spaced. Full or 1/3 Neutral.
Binder Tape: A suitable polyester tape
Jacket: Overlying (sleeve) black polyvinyl chloride (PVC).